7 posts • joined 13 Apr 2008
NEVER buy a Fiat
Fiats may be nice when brand new, but their build quality is crap.
Massive clutch problems.
Air mass sensor failure.
Wheel bearing failure.
Gearstick to gearbox linkage failure when crossing 3 lanes of traffic (no prior warning).
2 separate occasions when an engine sensor failure dumped us out on the M1.
This was despite having the car from new and dealer servicing throughout.
Fiat: Just say NO!
If the problem is too many people, how many should we have?
If the problem is too many people, then on what basis do you decide the optimum population size for the UK? How would you decide what the maximum, minimum or optimum population size should be? What factors should be included?
It is standard ranting to say "The UK has too many people, so we must do <horrible thing>", and a quick trip to a Godwin. I do not want to start that kind of a flame war. I want to know how you decide, because I've never seen it discussed.
If you think a baby translator is a good idea
If you think a baby translator is a good idea, then see this comic:
Whoops, somebody already posted that!
Sounds like botched distribution engineering to me
A site like this will have a high voltage distribution network, operating at 11kV, perhaps with a backbone at higher voltage, e.g. 66kV. In order to provide redundancy, much of the network will be interconnected so that it is possible to switch off any single part such as a breaker, substation or cable for maintenance without affecting users. A major consideration in such networks is fault level. This is the current that will flow into a short circuit until a fuse or breaker interrupts it. Obviously the fuse or breaker has to be rated to interrupt the fault current, which may be in the mega amp range, otherwise you get the kind of failure described here.
What is sometimes not obvious is that the more interconnected the network is, the harder it is to estimate the fault level accurately, and the easier it is to exceed equipment fault interruption ratings by having all the links closed. High fault capacity switchgear is expensive, and will generally not be installed at the lower levels of the network. I suspect that for the reasons stated by others, tight cost control, poor project management and security paranoia have combined to produce an unmagageable distribution network.
The intersection of two major power corridors probably complicates the whole issue as well.
There is a procedure called "Phasing Out" to counter precicely this problem. Even so, equipment should be rated to interrupt fault current without damage to non-wearing parts.
Once an ionised path has been established, 11kV goes exactly where it wants and will chew up EVERYTHING.
Where is The Thing?
The John Carpenter one.
Who will want to do a PhD when they have >£27k debt?
The point that worries me is that there will be very few people applying for UK PhD's when they already have interest on a >£27K loan ticking away after finishing their first degree.
With this cut in funding I think that the government is recognizing that there will be fewer applicants for however many places remain.
What the full force of RIPA should be used for..
Is catching the dirty bastards who fail to clean up after their dogs. And then make them eat it up with a spoon.
- Product round-up Ten excellent FREE PC apps to brighten your Windows
- Review Tough Banana Pi: a Raspberry Pi for colour-blind diehards
- Analysis Pity the poor Windows developer: The tools for desktop development are in disarray
- Product round-up Ten Mac freeware apps for your new Apple baby
- Chromecast video on UK, Euro TVs hertz so badly it makes us judder – but Google 'won't fix'